IET
 Topic Title: RCD problem Topic Summary: Ohms law Created On: 17 January 2014 08:37 PM Status: Post and Reply Linear : Threading : Single : Branch
 << 1 2 Previous Last unread
Search Topic
Topic Tools
 View similar topics Print this topic.
 18 January 2014 06:26 PM WiredScience Posts: 209 Joined: 25 January 2012 +1 for an earth leakage clamp meter. I recently clamped a single RCD+15MCB installation which was randomly tripping. IR of whole board lives to earth > 120MOhms. Measured leakage 21 mA with all the PCs, TVs, games and gadgets on. Supply voltage at time of measurement was 234V. The (unloaded) RCD consistently tripped at 22mA when ramp tested. Assuming a linear relationship between supply voltage and leakage current, then a 5% increase may cause a trip. 18 January 2014 07:37 PM Jaymack Posts: 5075 Joined: 07 April 2004 Originally posted by: WiredScience Assuming a linear relationship between supply voltage and leakage current, then a 5% increase may cause a trip. Any increase at all in voltage or decrease in the resistance, will cause a trip; if the circuit was already on the threshold of tripping the RCD. Regards 18 January 2014 07:55 PM Phillron Posts: 1388 Joined: 18 January 2007 There is a pecking order for suspicion when intermittent and witching hours tripping occurs The top of the list is appliance fault The top of that list is the Fridge freezer The suggestion of using a clamp meter,unfortunately it needs a lot of patience to stand there watching and waiting until that freezer stat decides to let the whole of its function become part of your game Your meters have not revealed your problem and likely will not do so Run that appliance from a different source for a few nights and see what developes 19 January 2014 07:44 PM Jaymack Posts: 5075 Joined: 07 April 2004 Originally posted by: Phillron There is a pecking order for suspicion when intermittent and witching hours tripping occurs In my personal experiences for tripping RCD's at any time, are heating grills, electric irons, electric ovens, tumble dryers and toasters are top contenders. (All with heating elements). Regards 20 January 2014 10:17 PM AJJewsbury Posts: 13117 Joined: 13 August 2003 if I ramp test it and it trips at say 26mA it will need an resistance on the circuit of 9230ohms or less to trip the rcd Yes (L-earth, presuming 240V). - Andy. 21 January 2014 12:16 PM WiredScience Posts: 209 Joined: 25 January 2012 Originally posted by: AJJewsbury if I ramp test it and it trips at say 26mA it will need an resistance on the circuit of 9230ohms or less to trip the rcd Yes (L-earth, presuming 240V). - Andy. Not forgetting that the d.c. tester won't measure the true impedance at 50Hz, so there may well be some disparity between calculated and actual leakage current. 31 January 2014 08:15 PM Grumpy Posts: 589 Joined: 09 January 2009 Sorry to resurrect an ageing post. Was called back to a job where I had replaced a pendant with a fluorescent. Three months later, when it was switched on it tripped the RCD. It was loop in to switch so easy to test switch to lamp cable, IR 0.2Mohm. Ohms law gives 1.15 mA. So why would that trip a 30mA RCD? Je pose ma valise from my first response. ------------------------- Only dead fish go with the flow. Be a salmon! 03 February 2014 03:32 PM AJJewsbury Posts: 13117 Joined: 13 August 2003 It was loop in to switch so easy to test switch to lamp cable, IR 0.2Mohm. Ohms law gives 1.15 mA. So why would that trip a 30mA RCD? Just one guess - during startup the fluorescent generated a higher 'striking' voltage - if that was across the fault a lot more that 1.15mA might flow? - Andy. 03 February 2014 04:30 PM webbix Posts: 134 Joined: 29 October 2006 Many thanks for all your advice. after having tested the ring upon reconnecting the washing machine with the machine switched off it tripped . then after resetting RCD i plugged the unplugged machine several times on about the 5 attempt it tripped again. it failed the PAT test earth leakage 0.26mA but trips after several attempts DEFO the machine . But why it trips in middle of the night when not switched on (but plugged in) i dont know!! john
IET » Wiring and the regulations » RCD problem

 << 1 2 Previous Last unread
Topic Tools
Statistics