IET
 Topic Title: Sub-main cut - Cables being joined using an Isolator Topic Summary: Created On: 16 May 2013 12:29 PM Status: Read Only Linear : Threading : Single : Branch
Search Topic
Topic Tools
 View similar topics Print this topic.
 16 May 2013 12:29 PM calumbtw Posts: 90 Joined: 22 October 2012 Hi, Part of a lv sub-main cable was cut & stolen. We have decided to install an isolator between the new cable supplied from the switchgear, and the rest of the existing cable that feeds the DB. Never come across this..how do I calculate the volt drop? Should they be two separate cables or calculated as one? Should they be the same size etc? Any regulations reg. this? Sorry if I haven't made it clear...any help would be appreciated. Thanks. 16 May 2013 12:49 PM AJJewsbury Posts: 16083 Joined: 13 August 2003 how do I calculate the volt drop? Should they be two separate cables or calculated as one? Assuming that the new cable is the same c.s.a. etc as the old one, it doesn't matter - you can calculate it either way and the answers should add up the same. If the new cable is different from the original, you'd have a different mV/A/m figure to work with, so you'd have to do it as two different sections and add the results together. - Andy. 16 May 2013 12:52 PM perspicacious Posts: 7854 Joined: 18 April 2006 Did the last PIR or EICR carried out on this cable before it was stolen raise any concerns about it being the incorrect size? Regards BOD 16 May 2013 01:12 PM calumbtw Posts: 90 Joined: 22 October 2012 Originally posted by: AJJewsbury how do I calculate the volt drop? Should they be two separate cables or calculated as one? Assuming that the new cable is the same c.s.a. etc as the old one, it doesn't matter - you can calculate it either way and the answers should add up the same. If the new cable is different from the original, you'd have a different mV/A/m figure to work with, so you'd have to do it as two different sections and add the results together. - Andy. Ok, thanks for that Andy Originally posted by: perspicacious Did the last PIR or EICR carried out on this cable before it was stolen raise any concerns about it being the incorrect size? Regards BOD Nope not that I am aware of. Thanks for the help!
 IET » Wiring and the regulations » Sub-main cut - Cables being joined using an Isolator Topic Tools
Statistics