
Electrician
 City of Bristol
 C. £31,729 per annum plus supplements, benefits and overtime
You’re a good team worker with a strong technical capacity – so bring your talents to a new role with one of the area’s leading employers.
 Recruiter: The Bristol Port Company

Supply Restoration Team Manager (HV/SAP)
 Oxford, Oxfordshire
 Salary: £37,588 to £49,645 + Car (SSE8) Depending on skills and experience
SSE is looking to recruit a Supply Restoration Team Manager to join our existing team in Oxford.
 Recruiter: SSE

Electrical Technical Lead  Global Operations, Engineering & Laboratory
 Kent
An exciting opportunity has arisen to join a dynamic team of professional engineers, supporting the development of novel drugs.
 Recruiter: Pfizer Ltd
IET 
search :
help :
home


Latest News:


Topic Title: Adding Currents Topic Summary: Is it right to add currents as values? Created On: 10 January 2013 02:39 PM Status: Post and Reply 
Linear : Threading : Single : Branch 

Search Topic

Topic Tools

10 January 2013 02:39 PM


Hi to all.
Imagine that we have a supply cable that feeds the main busbars of a switchboard. Lets also say that from these busbars depart 3 secondary supply cables that feed three motors, say A,B and C. Lets assume that Ia=10 A, Ib=20 A and Ic=30A are the nominal currents of the motors. Could we say that the supply cable is charged with 10+20+30=60A and start the calculations about the CSA with this number??? These are the rms values of the motor currents that are vectors and so the correct sum should be I = Ia+Ib+Ic but with the currents as vectors and not as rms values. Is there any possible explanation why I should just add rms values in order to find the current of the supply cable? I have heard a fellow engineer saying this thing but I do not agree and I would like to discuss it in here in case there is some simple explanation that I ignore. Thanks! 



10 January 2013 03:00 PM


The current loading will be cummulative as more and more load is designed/added for/to a DB. You have diversity in your favour for submain cables but VD, starting currents, EFLI and other factors can work against you.
 Empty barrels make the most noise. 



10 January 2013 03:12 PM


Sorry my friend but I do not believe that your answer fits my question. Either this or I do not understand exactly what you say. My question was rather different but anyway thank you!!




10 January 2013 03:55 PM


First of all
are we talking of three phase loads or single phase loads spread across three phases ? Are each of these loads operated at the same time or are they operated at separate times? Legh  http://www.leghrichardson.co.uk deavatared 



10 January 2013 04:18 PM


Yes, sorry, my mistake.
We are talking about 3 phase loads that can be run simoultaneously. Not all the time, but their operation can be some times at the same time. 



10 January 2013 05:18 PM


Vectors are for mechanics  phasors have been the preferred term in most text books. Phasors rotate whilst vectors are generally static.
Anyway to address your question  as you are probably aware the motor loads are inductive and the current will be displaced from the voltage (assuming this is our reference) by an angle  the 'phase angle'. The cosine of this angle is equal to the power factor of the motor if we can assume sinusoidal conditions. Each motor will have individual characteristics and so the power factors may be different for each motor and this will also vary with loading. If the motors are all around the same size and have similar characteristics then summing the currents arithmetically will not introduce much error. However, strictly speaking the currents should be summed as phasors (vectors) so as to take account of any difference in angle from the reference. Regards Geoff Blackwell 



10 January 2013 08:01 PM


Could we say that the supply cable is charged with 10+20+30=60A and start the calculations about the CSA with this number? These currents are not additive for A.C. currents, they are the resultant of the true currents and the imaginary currents, the magnitude of these depends upon the power factor  Cos phi. As a starting point, see the "j notation" for single phase application. Z = R + jX etc., (Impedance, Resistance and Reactance). The currents can't be added as explained above. Apart from the thermal running currents for cable sizing, the voltage drop on starting for the motors, is very important and requires to be considered; and whether staggered starting is possible, to alleviate summation of these starting currents etc. etc. The power factor and torque output on D.O.L. S.C. motor starting is very low; if the voltage drop is excessive i.e. >30%, the motor/s may not start at all. BTW "Fellow engineer" implies being nonelectrical due to the lack of understanding shown. Regards 



10 January 2013 11:06 PM


Thank you
That is exactly what I am telling in my first post. No can add just values. These are in deed imaginary numbers, or phasors as GeoffBlackwell said. I just wanted to know if there was any simple explanation that could lead in such a "simplification". 



11 January 2013 07:00 AM


Thank you That is exactly what I am telling in my first post. No can add just values. These are in deed imaginary numbers, or phasors as GeoffBlackwell said. I just wanted to know if there was any simple explanation that could lead in such a "simplification". and in your first post A word of caution before you tell all of your fellow engineers that they are wrong . When you are designing an installation many assumptions may have to be made. The design can involve a great deal of time and someone has to pay for this. So if the process can be speeded up by making 'engineering judgements' this will be done provided the overall design is not compromised. Take the example of selecting cable sizes  the solution i.e. the optimium cable size  will evolve after considering various factors. These factors will doubtless contain simplyfing assumptions (the adiabatic equation being a good example ). The end result of this process is a cable size, but you must bear in mind that cables are not made in an infinite range of sizes, they are made to preffered sizes (normally based on some mathematics) such as: 10.0; 16.0; 25.0; 35.0 and so on usually up to 400.0 (all sizes in square millimetres). So there is little point in directing too much effort to a cable size if the solution is going to be finally determined by a particular size availability. So if initial calculations suggest a 90.0mm2 cable there is little point in trying to reduce it as the size below is 70.0mm2  a 95.0mm2 is going to be required. If the initial calculations suggest a 98mm2 cable there may be some point in trying to improve the accuracy of the calculations by using a more complex approach as this may allow the use of a 95mm2 cable. If your fellow engineers are referring to a group of motors with similar sizes and characteristics their simplification may be acceptable. If not a more accurate approach is needed. Regards Geoff Blackwell 



11 January 2013 07:51 AM


Can some one do a sum , because I think Im missing the point.
I know what phasors and power triangles are. Could you not just add up the KW and times by PF. 



11 January 2013 09:25 AM


If your fellow engineers are referring to a group of motors with similar sizes and characteristics their simplification may be acceptable. Acceptable for "engineers"? not professional if from the electrical discipline. Regards 



11 January 2013 09:50 AM


Sums for zeeper
As Jaymack indicated above  the design of motor circuits can be complex  so simple answers will not suffice for a 'real world' design. However, the principles can often be extracted and simplified to allow learning to progress. So with that in mind a simple example may help. Consider two loads  both have inductive characteristics (they could be motors, but lets not go there ). Load A has a full load current of 10A and a full load power factor of 0.8 lagging. Load B has a full load current of 10A and a full load power factor of 0.6 lagging. These loads are connected to a remote distribution board and your task is to determine the magnitude of the current that will flow in the distribution circuit (submain) supplying the remote DB  when both loads are demanding their full load. If you think the answer is 20A you have some way to go before you achieve enlightenment . Both loads have some inductance and this causes the power factor to decrease from the value of 1.0 associated with resistive loads. However they have different power factors which implies that the inductive elements of each load are not the same. This means that the angle between voltage and current for each load will differ. Now when considering this problem we need to establish a reference so that we can determine the phase difference or phase angle differences for each current. The supply voltage is common to both loads at the origin of the system so the voltage phasor is our common reference. The angles between voltage and currents are referenced to this voltage. For sinusoidal waves the power factor is numerically equal to the cosine of phase angle between voltage and current. So for Load A: Phase Angle = arccos(0.8) = 37 degrees Load B: Phase Angle = arccos(0.6) = 53 degrees So if we were to sketch the phasor diagram using the voltage as a horizontal reference  current A would have magnitude 10 but lagging phase angle 37 degrees and current B would have magnitude 10 and lagging phase angle 53 degrees. The current in the distribution circuit will be the phasor sum of these two current and it will be less than 20A . Current A = 10A @ 37 degrees Converting Polar to Rectangular = R8.1 + j 5.9 Current B = 10A @ 53 degrees Converting Polar to Rectangular = 6.0 + j8.0 Total Current = (8.1 + j5.9) + (6.0 +j8.0) = 14.1 + j13.9 Converting Rectangular to Polar = 19.8A lagging the voltage by 44.6 degrees Now, and here is the rub, look how close our answer is to 20A  was it worth the effort . Note if you don't understand j notation just draw it out. Jaymack  no comment . Regards Geoff Blackwell 



11 January 2013 10:27 AM


Correct example, taking into account an even distribution of the loads between the three phases. But let us assume (because we engineers never rest ) that the one of the two loads is single phase and not three phase. What happens in this case??? One of the three phases shall be charged a little bit more than the others isn't it?
The whole previous analysis of your example was based on the single phase equivalent circuit where we assume that the current in all phases has the same magnitute and from phase to phase the currents differ only by a 120 degree angle. What happens if one or more of the loads are single phase? Obviously you cannot use the single phase equivalent circuit since at least one phase is different now. (Is there any chance I do not remember the electrical circuit analysis well? In this case ignore my small analysis...) 



11 January 2013 10:42 AM


If you are sizing a 3 phase distributor that has some single phase loads you need to identify the worst case (highest loading) for each phase and then size the cable on the highest single phase value.
Regards Geoff Blackwell 



11 January 2013 11:21 AM


Hi Geoff
Am i right in saying that the more motors added to an electrical system has an effect on the total power factor of the system. e.g. You have added two motors together and now have an angle of 44.6 degrees, which now gives a power factor of 0.71 lagging. Am i right in thinking this ?? 



11 January 2013 11:25 AM


Of course.
Each and every time that you add loads with different power factors, the final power factor is different from the previous ones. Only when you add loads with the same PF you get a final load with the same PF. 



11 January 2013 12:16 PM


Thanks Geoff
You lost me at the converting polar. They not teach that on my course lol. Think I need to go back to school, I managed to get to 45 degrees using my fingers, but when I draw the phasor the result keeps coming back as 14A. I think I may have over simplified or missed a step. But I was surprised that a lag of 44.6 was only worth 0.2A I think I'll stick with the current rating on the motor ID plates and worry about the start up voltdrop instead. 



11 January 2013 02:25 PM


I think this is how it's worked out (Pythagoras)
r√(x^2+y^2 ) = √(14.1^2+13.9^2 )= 19.79 Amps Regards 



11 January 2013 02:38 PM


That is correct. In fact this is part of the procedure of converting an imaginary number into polar mode.
The angle is also given by arctan (Im / Re) but I do not remember it by heart....(too much time since I last used it) 



11 January 2013 02:44 PM


Hi to all. Imagine that we have a supply cable that feeds the main busbars of a switchboard. Lets also say that from these busbars depart 3 secondary supply cables that feed three motors, say A,B and C. Lets assume that Ia=10 A, Ib=20 A and Ic=30A are the nominal currents of the motors. OK  that's the load per phase Could we say that the supply cable is charged with 10+20+30=60A and start the calculations about the CSA with this number??? Yes  remembering that's the load per phase These are the rms values of the motor currents that are vectors and so the correct sum should be I = Ia+Ib+Ic but with the currents as vectors and not as rms values. they are RMS values but at this point we aren't concerned with the vectors because we are only worried about the load per phase and select a 3 phase cable from tables. Is there any possible explanation why I should just add rms values in order to find the current of the supply cable? every possible explanation, because that's the current you are trying to find. I have heard a fellow engineer saying this thing but I do not agree and I would like to discuss it in here in case there is some simple explanation that I ignore. for this task, I suspect your engineer ir right. In your example you need a cable that can carry 60A per phase  and it's possibly just a 3 core as the motor loads present a balanced load so the neutral current is zero. So, if using armoured cable as a example, you would need something along the lines of a 16mm3 3 core XLPE/SWA/LSF cable  (we'll leave the issue of the circuit protective conductor to another thread. Thanks! regards OMS  Let the wind blow you, across a big floor. 



IET
» Wiring and the regulations
»
Adding Currents

Topic Tools

FuseTalk Standard Edition v3.2  © 19992016 FuseTalk Inc. All rights reserved.