
Electrical Machine Designer
 Norwich, Norfolk
Seeking experienced or graduate electrical machine designer
 Recruiter: PPI Engineering Limited

Engineering Manager  Naval Architect
 England, Cumbria, BarrowInFurness
 Competitive package
As an Engineering Manager  Naval Architecture you will be managing the Whole Boat Architecture and Concepts team tasked with supporting the delivery of the remaining Astute submarines, and developing new technology for future submarine programmes.
 Recruiter: BAE Systems

Materials Scientist
 Essex, Chelmsford, England
 Competitive package
BAE Systems are currently recruiting for a Materials Scientist to join the team based in Great Baddow, Chelmsford, reporting directly to the PARC Supervisor.
 Recruiter: BAE Systems
IET 
search :
help :
home


Latest News:


Topic Title: Formula Factor Topic Summary: Anyone know what 0.48 represents? Created On: 31 December 2012 02:20 PM Status: Post and Reply 
Linear : Threading : Single : Branch 
Search Topic

Topic Tools

31 December 2012 02:20 PM


In 5.1.2 of appendix 4 page 309 (BS 7671) there are details of the different formulas for calculating grouping factors, and equation 4 has a factor of 0.48 Ib squared (sorry can't seem to add a superscript 2), does anyone know what this 0.48 represents? I have quite a good library of text books and some of them refer to this formula but not one states where this factor is derived from. Neither can I find it on the web.
Cheers SL 



31 December 2012 03:21 PM


I think it will be a correction factor in the equation, there are examples of its use in the IEE Electrical Installation Design Guide  calculations for electricians, p.49.
From a quick read, using the equation will allow grouped cables to be smaller, as it is very unlikely for them all to be subject to overload at the same time. The example there shows Ib divided into the Cg.. factors, and giving a resulting It of 27.5A, the '0.48' equation gives a result of 24.7A for the same circuits, with the result being a cable capable of carrying 27.5A is needed, the larger result being the one required. Comparing the results from Equation 2, and 3&4, Eq2 gives a current of 33.3A, Eq3&4 27.5A, so a smaller cable size is available if you do the longer calculations. So, being as there is a lot of squaring and square root in the equation, a correction factor would be my best assumption. 



31 December 2012 08:02 PM


In 5.1.2 of appendix 4 page 309 (BS 7671) there are details of the different formulas for calculating grouping factors, and equation 4 has a factor of 0.48 Ib squared (sorry can't seem to add a superscript 2), does anyone know what this 0.48 represents? The second part of the equation, looks like that for the calculation of an RMS value for heating effect. It could be a fudge factor from thermal modelling, as mathematicians are prone to do. But who would use the calculations in the practical sense, when tables are available? Regards 



02 January 2013 09:34 AM


Hi Gents
Thanks for your views on this and confirming basically what I thought anyway. My reason for inquiring was purely curiosity as I was a bit bored over the Xmas period. Sad I know! Cheers and happy new year SL 



02 January 2013 07:15 PM


Id say its a Nusselt Number, Look up Churchill, Prandt, Rayleigh.
If you think you were bored, you will be 



04 January 2013 08:44 AM


Hello.
1.45 is the current causing effective operation of the protective device (see 433.1.1). In the derivation of the appendix 4 formula 1.45 ends up being squared and appears in the denominator, this is the same as multiplying by [1 divided by 1.45 squared] which equals 0.4756.... which rounds up to 0.48. 


IET
» Wiring and the regulations
»
Formula Factor

Topic Tools

FuseTalk Standard Edition v3.2  © 19992016 FuseTalk Inc. All rights reserved.