
Software Technical Lead
Premium job
 Hanslope Park, Milton Keynes
 £40,722 to £53,575 + £5k Welcome Package
From the smallest details to leading the biggest decisions, your impact will be out of this world.
 Recruiter: HMGCC

Electronics Engineer – Cambridge & Antarctica
Premium job
 Cambridge & Antarctica
 In the range of £28,200 to £30,600 per annum.
With the launch of our new research vessel, the RRS Sir David Attenborough, we are looking for Electronics Engineers to support our ongoing science
 Recruiter: British Antarctic Survey

IT Engineer – Cambridge & Antarctica
Premium job
 Cambridge & Antarctica
 In the range of £28,200 to £30,600 per annum.
IT Support Engineers are required to manage and support the computer systems and information technology facilities used within BAS
 Recruiter: British Antarctic Survey
IET 
search :
help :
home


Latest News:


Topic Title: Formula Factor Topic Summary: Anyone know what 0.48 represents? Created On: 31 December 2012 02:20 PM Status: Read Only 
Linear : Threading : Single : Branch 
Search Topic

Topic Tools

31 December 2012 02:20 PM


In 5.1.2 of appendix 4 page 309 (BS 7671) there are details of the different formulas for calculating grouping factors, and equation 4 has a factor of 0.48 Ib squared (sorry can't seem to add a superscript 2), does anyone know what this 0.48 represents? I have quite a good library of text books and some of them refer to this formula but not one states where this factor is derived from. Neither can I find it on the web.
Cheers SL 



31 December 2012 03:21 PM


I think it will be a correction factor in the equation, there are examples of its use in the IEE Electrical Installation Design Guide  calculations for electricians, p.49.
From a quick read, using the equation will allow grouped cables to be smaller, as it is very unlikely for them all to be subject to overload at the same time. The example there shows Ib divided into the Cg.. factors, and giving a resulting It of 27.5A, the '0.48' equation gives a result of 24.7A for the same circuits, with the result being a cable capable of carrying 27.5A is needed, the larger result being the one required. Comparing the results from Equation 2, and 3&4, Eq2 gives a current of 33.3A, Eq3&4 27.5A, so a smaller cable size is available if you do the longer calculations. So, being as there is a lot of squaring and square root in the equation, a correction factor would be my best assumption. 



31 December 2012 08:02 PM


In 5.1.2 of appendix 4 page 309 (BS 7671) there are details of the different formulas for calculating grouping factors, and equation 4 has a factor of 0.48 Ib squared (sorry can't seem to add a superscript 2), does anyone know what this 0.48 represents? The second part of the equation, looks like that for the calculation of an RMS value for heating effect. It could be a fudge factor from thermal modelling, as mathematicians are prone to do. But who would use the calculations in the practical sense, when tables are available? Regards 



02 January 2013 09:34 AM


Hi Gents
Thanks for your views on this and confirming basically what I thought anyway. My reason for inquiring was purely curiosity as I was a bit bored over the Xmas period. Sad I know! Cheers and happy new year SL 



02 January 2013 07:15 PM


Id say its a Nusselt Number, Look up Churchill, Prandt, Rayleigh.
If you think you were bored, you will be 



04 January 2013 08:44 AM


Hello.
1.45 is the current causing effective operation of the protective device (see 433.1.1). In the derivation of the appendix 4 formula 1.45 ends up being squared and appears in the denominator, this is the same as multiplying by [1 divided by 1.45 squared] which equals 0.4756.... which rounds up to 0.48. 


IET
» Wiring and the regulations
»
Formula Factor

Topic Tools

New here?
See Also:
FuseTalk Standard Edition v3.2  © 19992017 FuseTalk Inc. All rights reserved.